Heating and cooling with energy piles
– thermal use of the ground
An energy pile plant should preferably be used as alternating storage system (heating or cooling operation, depending on the season). Thus, an optimum specific extract performance [W/m] either for heat or coldness production can be reached. The temperature regime of the energy pile plant can be designed in a sustainably stabile way. A well-adjusted heat balance over many years minimizes the mutual thermal effect of neighbouring energy piles.
Seasonal storage cycle
For cooling operations, the selected active temperature levels should be as high as possible for cooling (> 16...18°C) - and as low as possible for the heating operations (< 35°C). Thus, a high energy efficiency of the geothermal pump can be reached. Optimum active temperature levels in buildings may advantageously be created by low-temperature heaters, activation of thermal mass, extensive fan-registers etc.